TKF-25Y split elevator air conditioner parmeter :
|Rated Cool Capaticy (W )||2500W|
|Air Flow (m3/h )||480 (high wind ) / 360 (low wind ) m 3 /h|
|Rated Input Current (A )||4.7A|
|Rated Input power (W )||1015w|
|Voltage/Frequency||220V - 50Hz|
|Noise dB (A )||Main unit ï¼œ 55 dB (A )||subsidiary ï¼œ 50 dB (A )|
|Dimensions (L*W*H ) mm||Main machine||subsidiary|
|450*310*395 (mm)||556*238*235(mm )|
|Air out Opening Size||435* 45mm|
|Return Air Opening Size||Ñ„ 200mm circular hole or 620mm perimeter ellipse|
|Weight (kg )||Main machine 31.5 (Kg )||subsidiary 15.5 m (Kg )|
|For Elevator (kg )||â‰¤ 1350kg|
Brief Installing introduction:
1 ï¼Ž the main machine of the elevator air conditioner are installed on the upper beam of the elevator or fix by the rack to the upper beam.
2 ï¼Ž open an 200mm hole on the elevator car top for returning air.
3 ï¼Ž Tear off the original fan, heat insulating dealing to the car top interlayer, fix the subsidiary to the fan opening.
4 ï¼Ž lead the core of the remote receiving probe to car and fix it ;
5 ï¼Ž connect the copper pipe,condensate water pipe and electricity wire between the major machine and the subsidiary ;
6 ï¼Ž screw open the adjust vavle, discharge the air in the pipe and screw tight it ;
7 ï¼Ž Connect the power supply, use remote controller to set the running mode of â€œprogram controlâ€, the air conditioner goes into auto running mode.